Hi,all!There is power factor controller on LV network.A group of outputs...which control contactor for stages of capacitor banks...is not working...the reason is not interesting...loose connection somwhere inside the controller...Is there any technical reasons...not to connect 2 contactors...with two capacitor bank groups on same output of controller?Becouse...there is half of outputs....which are in work.It is clear..that with this kind of grouping...tunning will not be so fine....like with double outputs...but for a period of time..is it possible to work on half of controller outputs?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Learn methods and guidelines for using stereolithography (SLA) 3D printed molds in the injection molding process to lower costs and lead time. Discover how this hybrid manufacturing process enables on-demand mold fabrication to quickly produce small batches of thermoplastic parts. Download Now
Examine how the principles of DfAM upend many of the long-standing rules around manufacturability - allowing engineers and designers to place a partâ€™s function at the center of their design considerations. Download Now
Metal 3D printing has rapidly emerged as a key technology in modern design and manufacturing, so itâ€™s critical educational institutions include it in their curricula to avoid leaving students at a disadvantage as they enter the workforce. Download Now
This ebook covers tips for creating and managing workflows, security best practices and protection of intellectual property, Cloud vs. on-premise software solutions, CAD file management, compliance, and more. Download Now