×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# High Impedance Differential CT

## High Impedance Differential CT

(OP)
If one of the CT is fully saturated for an external fault condition, there would be difference in the currents from the two CT's and if the difference is more than the Pickup, the differential relay trips, as in the following picture,

I read in a literature that, "The knee point voltage (Vk) for class PX CT's used in high impedance scheme is calculated for the worst condition that one of the CT's is fully saturated and the other CT has to develop enough voltage to drive current through the other CT circuit to ensure stability during external fault"

Why the other CT has to develop enough voltage to drive the current through the other CT?

### RE: High Impedance Differential CT

Why would you apply a high impedance differential on a transformer this way?

### RE: High Impedance Differential CT

I think you are looking at a picture for a low impedance relay. Below is a picture for a high impedance relay.

In a high impedance scheme, once one of the CTs saturate, the current is going to flow through that CT instead of the high impedance ,that you are measuring the voltage off of to determine if you should trip. The measured tripping voltage than drops due to the ease the current flows through the saturated CT. When a CT saturates, it basically decouples the primary and secondary and acts like an open air inductor.

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!