For example i only have 6 FHC in a fireprotection system, how much gpm i need to supply them? what i understood in NFPA 14, 500gpm at the most remote standpipe (2 FHC operational) plus additional 250gpm per additional standpipes. (the system is looped by the way) that will give me 1500gpm? i think im wrong. Please explain, thanks.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.