Does NEC forbid using a disconnect switch for both protection and unit operation? Typically we would have a separate disconnect and ON/OFF switch but it has been suggested to combine these two. It doesn't sound right but I couldn't find in the NEC where it was explicitly forbidden. Any help on this would be appreciated.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.