4 LPs at 37 meters are designed a sump pump for a new project. I just looked at their submission, and from what I can tell, the system head curve isn't shown. This pump will move water at the design head at a rate of 32 l/s instead of 4 l/s, and both the power input and NPSR will go up. The hydraulic data does not match what was asked for or what was planned. If I'm wrong, please correct me.https://res.cloudinary.com/engineering-com/image/upload/v1672298787/tips/wilo_sump_pump_bfypdf.pdf
The problem with the world is that intelligent people are full of doubts, while stupid ones are full of confidence.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.