×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# Fan Inlet Connection Loss Coefficient

## Fan Inlet Connection Loss Coefficient

(OP)
Hello all. I'm looking into the pressure drop associated with a lab exhaust system that was just installed (see picture below). Specifically, I'm stuck now on the pressure drop that occurs the last 4-gore elbow to the exhaust fan inlet. The exhaust fan is a centrifugal blower. Having perused this online forum and the available ASHRAE books (I do not have the duct fitting database unfortunately), I'm not sure what method to use to find the total pressure drop from the elbow to the inlet of the fan. There are two approaches:

1. Use one of the ED7-* Fan Inlet loss coefficient tables provided by ASHRAE (I have ED7-1 or ED7-2). ED7-2 is the most applicable. For this approach (I think) I would not include the flexible duct connection/duct expansion joint or the round-to-round transition, as it appears to be covered by the ED7-2 pressure drop.
2. Or, I can calculate the pressure drop piece by piece. I would use an approximation based on the roughness of the duct expansion joint (neoprene) and table SD4-1 for the loss coefficient for the round-to-round transition.
Both of these approaches seem unsatisfactory because, Approach 1 does not account for the duct expansion joint and the round-to-round transition while Approach 2 does not account for the Fan System Effect Coefficient. I believe there will be a Fan System Effect Coefficient because the 5*d (d=diameter of duct=12"Ø in this case) length requirement (by requirement I mean rule of thumb in the office, because I have also seen that 3*d may be sufficient in other cases-this may depend on the type of elbow) for the straight duct to develop laminar flow after the elbow was not met.

Does anyone have any guidance or advice on this issue?

### RE: Fan Inlet Connection Loss Coefficient

A sketch of the set up with identification of all the components mentioned in your OP would be a better approach instead of a picture. Also a performance curve of the fan which you can get from the manufacturer is needed to determine the pressure drop of the system.

### RE: Fan Inlet Connection Loss Coefficient

(OP)
Alright - not in the office right now. But when I get back, I'll provide a sketch (with their associated pressure drop ID or manual inputs) and a excel sheet that I put together. Thanks for the advice.

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

#### Resources

Low-Volume Rapid Injection Molding With 3D Printed Molds
Learn methods and guidelines for using stereolithography (SLA) 3D printed molds in the injection molding process to lower costs and lead time. Discover how this hybrid manufacturing process enables on-demand mold fabrication to quickly produce small batches of thermoplastic parts. Download Now
Examine how the principles of DfAM upend many of the long-standing rules around manufacturability - allowing engineers and designers to place a partâ€™s function at the center of their design considerations. Download Now
Taking Control of Engineering Documents
This ebook covers tips for creating and managing workflows, security best practices and protection of intellectual property, Cloud vs. on-premise software solutions, CAD file management, compliance, and more. Download Now

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!