×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# Distance limitation for control cables

## Distance limitation for control cables

(OP)
Ca we use cu 5CX2.5 mm2 control cable for Local Push Button Station at a distance of 480 Meter from Motor Control Centre . Control Supply voltage is 110VAC.

### RE: Distance limitation for control cables

That depends entirely on the circuit current load. Grounding requirements also apply.

The more you know, the more you know you don't know.

### RE: Distance limitation for control cables

Spoiler alert - if you read the threads Keith references, I suspect you'll find that 110 V ac pilot control at that distance will be problematic, regardless of wire size. DC control can work.

### RE: Distance limitation for control cables

Or, you have to put a shunt load on the cable to waste the coupled energy.

Keith Cress
kcress - http://www.flaminsystems.com

### RE: Distance limitation for control cables

Dear Mr. SYAMAL KUMAR SARBADHIKARI (Electrical)
" Can we use cu 5CX2.5 mm2 control cable for Local Push Button Station at a distance of 480 Meter from Motor Control Centre . Control Supply voltage is 110VAC."
1. Your question is on the [influence of the length of conductors used in contactor control circuit]. Under certain conditions the excessive length of the control circuit conductors may prevent the contactor from:
a) not closing: due to excessive voltage drop (in ac or dc),
b) not opening: due to excessive capacitance (in ac).
2. Influencing factors:
a) voltage, conductor size, length and the [pull-in VA of the contactor],
b) the wiring (e.g. via maintained push-button or via momentary push-button...). These may be caused by i) high control voltage, ii) low coil holding consumption, iii) low contactor dropout voltage, [the line capacitance etc....].
3. These information are published in the "contactor " catalogues of major contactor manufacturer, based on their own product.
4. Your data did not specified the [contactor(s) pull-in and holding VA].
Che Kuan Yau (Singapore)

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!