## Calculating volumetric flow rate without rotameter

## Calculating volumetric flow rate without rotameter

(OP)

Hi,

I'm wondering how You can calculate volumetric flow rate (SCFM=ft2/min) without rotameter installed.

We need to change from 1,625" to 1,25" Cold End. This will change the volumetric flow rate.

Liquid nitrogen is pumped by a hydraulic pump to a vaporizor. How can I calculate gasses volumetric flow rate out of vaporizor?

Thank You in advance!

I'm wondering how You can calculate volumetric flow rate (SCFM=ft2/min) without rotameter installed.

We need to change from 1,625" to 1,25" Cold End. This will change the volumetric flow rate.

Liquid nitrogen is pumped by a hydraulic pump to a vaporizor. How can I calculate gasses volumetric flow rate out of vaporizor?

Thank You in advance!

## RE: Calculating volumetric flow rate without rotameter

Pump rate?

Free flow rate?

What do you know? Anything?

If you know the mass rate, you can figure volume like this.

https://www.eng-tips.com/viewthread.cfm?qid=485439

## RE: Calculating volumetric flow rate without rotameter

General Specs of the Pump:Pump rotation: Bi-directional

Stroke: 1,375"

Max pump speed: 1200 RPM

Max power output: 200HP

Cold End bore size: 1,25"

Max discharge pressure: 15000psi

On the datasheet for vaporizor used, it states that:

- Gas ρ = 0,072 lb/ft3

- Specific volume = 13,8889 ft3/lb

- Vapor density = 0,967 and Liquid density@BP: 50,46 lb/ft3

I also read that liquid to gass expansion ratio of nitrogen is 1:694 at 20deg C.

The Bernoulli's equation is: P1+1/2ρv1^2+ρgh1=P2+1/2ρv2^2+ρgh2

Known data:

P1 = Pressure out of hydraulic pump

P2 = Pressure of gas coming out of vaporizor (backpressure)

ρ = density of fluid

g, h1 and h2

As I want to solve for v2, which is the velocity of the medium going out of vaporizor, I need one more input, v1. How can I obtain velocity of the fluid going in to the vaporizor?

Also, can I really use Bernoulli's equation if the density of fluid going in is different than density of gass coming out of vaporizor?

If my understanding is correct, having found v2, I can use v2 = q2/A = 4q/(D^2*π) or

q2 = (v2*D^2*π)/4 to find volumetric flow rate (q2). However, this equation only stands for flat, plane cross-sections. Otherwise, it's q = vAcosθ. Where θ is the angle between the unit normal n̂ and the velocity vector v of the substance elements.

Cheers and thank You!

## RE: Calculating volumetric flow rate without rotameter

I found out that the value I'm looking for is

notexactly the volumetric flow rate...The value I want to find is SCFM (Standard Cubic Feet Minute), which is not the same as volumetric flow rate, as I first thought.

SCFM is not dependant on either temperature or pressure, as it takes standard values for these. (P=1atm, T=68°F).

My former collegue came with the strange assumption that SCFM = 3*RPM of the pump. How can that be?

## RE: Calculating volumetric flow rate without rotameter

I would like to discover this one :)

https://www.azoft.com/blog/programming-languages-r...

## RE: Calculating volumetric flow rate without rotameter

So it does for me. I have no idea how he came up with this and he is no longer working here. I'll try to contact him and see what he responds. In the meantime I know that one can obtain CMF with this equation:

CMF = (CID*RPM*VE)/3456, where:

CID: Engines displacement(in^3)

VE: volumetric efficiency (VE=3 for engines with turbo, maybe he took value 3 from here?)

Even if ... SCFM = CFM*(P

_{actual}/14,7psi)*(68°F/T_{actual}) and he is taking the RPM from the hyrdraulic pump in his formula.## RE: Calculating volumetric flow rate without rotameter

P1 x V1 / T1 = P2 x v2 / T2

Solve for the value you want.

Pressures and temperatures are absolute values and compressibility is neglected.

Absolute temperature is °Rankin "R" degrees = F + 459.67

Compressibility will be important at high pressures. It is also gas dependent.

Pump displacement per minute is = Cylinder volume x rpm

If a piston pump doing gas compression, there is an initial volume of gas taken in when stroke is at 0 position. That amount of gas or liquid in the cylinder depends on the inlet pressure and temperature. The volume at the outlet depends on the discharge pressure.

When at full stroke, there is some additional length of the cylinder where the N2 is compressed to its new volume V2. Calculate that and you can find the pressure.

How have to estimate the temperature using the gas k value.

A liquid pump's capacity is cylinder displacement/stroke x rpm. Discharge pressure will be whatever pressure is needed for the liquid to get into the downstream piping. That's controlled by how you are operating that equipment and how that affects pressure at the pump discharge.

The data sheet values are for N2 at Standard conditions. N2 weighs 0.072 lbs/ft3 at STP.

The inverse of that is specific volume 13.8ft3, the volume needed to have a pound of air at STP. I guess the liquid N2 density is 50.46lbs/ft3

## RE: Calculating volumetric flow rate without rotameter

I can't operate with numbers. I have to come up with the equation that gives SCFM as an output.

The client wants to change cold ends from 1,625" to 1,25" on 901-01966 ICP-200 pump.

It seemed logical to me that this will change SCFM output. However, the equation my former collegue used was 3xRPM and this would imply that SCFM is independent of both pressure and temperature.

From the data chart of the pump, flow rate:pump speed is a linear function. We can write Flow Rate (GPM), as a function of RPM.

For Ø1.625 Cold Ends: Flow Rate (GPM) = 0,032*RPM

For Ø1.250 Cold Ends: Flow Rate (GPM) = 0,019*RPM

VAPORIZER SPECIFICATIONSCapacity: 180,000 SCFH

MAWP N₂: 15,000 PSI

MAWP H₂O: 150 PSI

H₂O Flow Required: 120-140 GPM

H₂O Temperature Required: 185° F

H₂O ∆T @ 120 GPM: 45° F

H₂O ∆T @ 140 GPM: 35° F

H₂O ∆P @ 140 GPM: 25-35 PSI

N₂ ∆P @ 180K & 10K PSI: 200 PSI

## RE: Calculating volumetric flow rate without rotameter

Weight of liquid in must equal the weight of gas out.If the liquid temperature is adjusted for 20deg C, then each stroke or revolution will deliver a known weight of nitrogen.

My WAG is that your colleague used the volume of one pump RPM to determine the weight of nitrogen per revolution.

He then calculated that That volume of liquid times 694 times 3 equalled 1 cu ft at SCF conditions.

I don't know what you mean by the "cold end". But, if the cold end change does not change the volume per revolution there should be no change in the weight per revolution.

If the cold end is a restriction, then the velocity of the gas will change but not the SCFM.

Weight in equals Weight out.If the cold end change does directly change the pump displacement per stroke, then the change in SCFM will be in the ratio of 1.25

^{2}/ 1.625^{2}= 0.592--------------------

Ohm's lawNot just a good idea;

It's the LAW!## RE: Calculating volumetric flow rate without rotameter

There are 3 cylinders, right?

I made a spreadsheet for you.

Pump discharge = cylinder volume x number of cylinders x rpm x volumetric efficiency

cylinder volume is 1/4 pi D^2 x stroke

volumetric efficiency 0.87 per your pump chart. A volumetric efficiency 0f 0.87 indicates that the stroke does not empty the cylinder completely. There will be 13% of the cylinder volume that will remain in the cylinder.

The pump will give you the calculated discharge up to the max pressures as per your chart. The pump apparently runs out of sufficient power for each cold end diameter at the pressures indicated.

DON'T USE THIS SPREADSHEET ATTACHED HERE.

GAS VOLUME IS GPM, NOT CFM.

I CORRECTED THE PICTURE, BUT CAN'T SEEM TO CORRECT THIS SPREADSHEET LINK.

THE CORRECTED SHEET FOLLOWS.

## RE: Calculating volumetric flow rate without rotameter

The other one has the wrong gas volume as cfm, but it is gpm

This one gives both like the picture above.

Gas volume is standard US gallons and standard cubic feet.

## RE: Calculating volumetric flow rate without rotameter

Good morning!

Wow, I did not expect that someone will give so much help to a stranger on the internet. Thank You so much! I really appreciate Your time spent on this. Any way I can give back to You? (tipjar, anything?)

After going through the spreadsheet, I now understand how the calculations should have been made.

Defining

Gas vol(cfm) in terms of RPM should then be:3,0194...*RPM for 1,625 cylinder diameter

1,7865...*RPM for 1,25 cylinder diameter

This proves that assumption 3*RPM that my collegue made was correct and that the value of SFCM is changed with piston diameter.

Thank You again!## RE: Calculating volumetric flow rate without rotameter

## RE: Calculating volumetric flow rate without rotameter

V

_{cmf}(D,RPM) = 1,1434241355938155786971828180212*D^{2}*RPM = 1,1434*D^{2}*RPMwhere D is piston diameter in inches.

## RE: Calculating volumetric flow rate without rotameter

## RE: Calculating volumetric flow rate without rotameter

I should probably stick with 1,14*D

^{2}*RPM## RE: Calculating volumetric flow rate without rotameter