×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# Getting Water Pressure at a Certain Height

## Getting Water Pressure at a Certain Height

(OP)
It's been some time since I've had to deal with this but I believe I'm doing it the same and correct way. I have a building with a Fire Pump (Electric). And make sure at what height we can stop using pressure-reducing valves.

Water Flow Test Static= 88
Fire Pump Churn= 119
Total: 207 PSI

Assuming the water flow test was taken at 0'-0 elevation and the building's First Floor, Ground for non-USA, is also 0'-0. Then with the pressure loss due to height would require 32 PSI which is ~73'.

I was just reviewing an older project in which I did the same calculation, to verify I was doing it right, and they stopped using pressure-reducing valves about 76' before I would have.

### RE: Getting Water Pressure at a Certain Height

Here is a quick / dirty calc:

207-175 = 32 psi

32 psi / .434 psi per foot = 74'. So, from the pump discharge up to ±75' you will need PRV for the hoses and control valves.

Travis Mack, SET, CWBSP, RME-G, CFPS
MFP Design, a Ferguson Enterprise
www.mfpdesign.com

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

#### Resources

Taking Control of Engineering Documents
This ebook covers tips for creating and managing workflows, security best practices and protection of intellectual property, Cloud vs. on-premise software solutions, CAD file management, compliance, and more. Download Now
The Great Project Profitability Debate
A/E firms have a great opportunity to lead the world into the future, but the industryâ€™s greatest assetâ€”real-time dataâ€”is sitting wasted in clunky, archaic ERP platforms. Learn how real-time, fully interactive dashboards in a modern ERP allow you to unlock data that will shape the future of the world. Download Now

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!