×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# IEC60364-5-52 Tabel B.52.18

## IEC60364-5-52 Tabel B.52.18

### RE: IEC60364-5-52 Tabel B.52.18

In the sketch, I see 20 circuits, i.e. 20 sets of cables each comprising of +ve & ve cable set.
If you are using single core cables (as it seems from sketch), don't space the cables of same circuit. That is keep the +ve & -ve cable of the same circuit together.
The spacing of one cable dia shall apply between the circuits and the corresponding derating factor is 0.35 from the table in the IEC code.
Spacing between +ve and -ve cable of the same circuit may lead to eddy currents (and resultant heating) in the metallic structures close to the trench whenever there is variation in the current flow.

### RE: IEC60364-5-52 Tabel B.52.18

There are 2 possibilities:
1)consider 2-conductor cable and treat it as 10 cables.
Let's say 120 square mm copper pvc insulated 2 conductors underground: 246 A [IEC 60364-5-52] . 12 cable 0.42 derating I=246*0.42=103.32 A.
2)20 circuits single core cables.
Since IEC 60364-5-52 does not present a table with single core cable, you have to calculate the rating of single core buried cable using IEC 60287-2-1 and IEC 60287-1-1. The conductor diameter and 20oC resistance from IEC 60228. Insulation and sheath [if any] according to IEC 60502-1 [low voltage].
I did now this calculation for the above-mentioned cable and I get 311 A. Multiply this by 0.35 for 20 cables I get 109 A [5.5% more]

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

#### Resources

Low-Volume Rapid Injection Molding With 3D Printed Molds
Learn methods and guidelines for using stereolithography (SLA) 3D printed molds in the injection molding process to lower costs and lead time. Discover how this hybrid manufacturing process enables on-demand mold fabrication to quickly produce small batches of thermoplastic parts. Download Now
Examine how the principles of DfAM upend many of the long-standing rules around manufacturability - allowing engineers and designers to place a partâ€™s function at the center of their design considerations. Download Now
Taking Control of Engineering Documents
This ebook covers tips for creating and managing workflows, security best practices and protection of intellectual property, Cloud vs. on-premise software solutions, CAD file management, compliance, and more. Download Now

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!