×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# Steam Generation Calculation

## Steam Generation Calculation

(OP)
Dear Experts,

I would like to ask you to correct my calculation and my interpretation if I am wrong. The question basically pertains to the increase in steam generation via increase in feed water temperature.

Currently, the feed water temperature is 85 C. I am thinking to increase it up to 95 C so that steam generation could be increased. The boiler is Waste Heat Recovery Boiler extracting energy from engine exhaust. The feed tank capacity is 2.7 MT. Calculation is as follows,

Energy saved there by increase feed water temperature by 10 C.

Q = 10 * 2700 * 4.186

Q = 113022 KJ

Now the steam pressure normally is 6.5 BAR. At this pressure, the specific ethalpy of steam is 2758.87 KJ/KG. Considering this, I would generate more steam of,

113022 / 2758.87 = 40 KG (approx.)

Which is very less as compare to my expectation. Please suggest am I correct?

Thanks.

### RE: Steam Generation Calculation

The energy in 1kg of steam at 6.5 bar is HUGE compared to 1kg of water with a temp rise of 1 C - 2758 vs 4.1 using your figures.
Heating water is relatively easy compared to making steam

So yes it will help, but by an incredibly small amount.

Remember - More details = better answers
Also: If you get a response it's polite to respond to it.

### RE: Steam Generation Calculation

(OP)
Thanks

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!