×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# CHW Pump Pressure3

## CHW Pump Pressure

(OP)
Had a heated argument so just want to have clear understanding on this thing. When we are calculating pressure head for chilled water pump, we include all fittings and losses occur through the farthest route of CHW piping with corresponding flow including the return lines. My understanding is, this pressure is nothing but the differential pressure we have maintain across pump (Discharge - Suction Pump)to get the desired supply flow (as per pump selection or curve)

### RE: CHW Pump Pressure

For a closed loop system where the pressure is maintained such that the highest point of the piping is kept at positive pressure - correct. You don't mention it specifically but also include losses through the AHU or whatever you plan to use the CHW for.

Remember - More details = better answers
Also: If you get a response it's polite to respond to it.

### RE: CHW Pump Pressure

Pump discharge pressure - Pump suction pressure= Differential head developed by the pump= System pressure drop

### RE: CHW Pump Pressure

(OP)
Thanks Folks...!!!

### RE: CHW Pump Pressure

Just pointing out a nuance - your index run may not be the furthermost point in the system. sometimes a closer item may have a higher pressure drop through it's coil and therefore become the system index. 99% of the time your statement is correct though.

(OP)
Correct. Thanks.

### RE: CHW Pump Pressure

(OP)
What are the possible reasons if i received correct flow but not correct differential pressure (as per the pump performance curve)?

### RE: CHW Pump Pressure

Different voltage

Variance in pump performance

Give us a bit of a clue here - how much different?

Remember - More details = better answers
Also: If you get a response it's polite to respond to it.

### RE: CHW Pump Pressure

Are you sure you are looking at the correct impeller size? Are you running at full rpm?

### RE: CHW Pump Pressure

(OP)
There are 3 pumps running. I could expect any one might have problem, but its unlikely that all three might have or may not have same issue. @pump 1: suction pressure is 2 bar and discharge is 5.3 bar. dP 3.3 bar. At 3.3 bar my flow to be 50 l/s as per performance curve, but in fact i am getting 75 l/s (which is req. as per design).

### RE: CHW Pump Pressure

I'm still confused by your reply. With three pumps (I assume in parallel) you will have a different flow characteristic than you would with only one pump running. Are you looking at the combined pump curves of all three in parallel?

### RE: CHW Pump Pressure

Can you post pump curve.

Also check the electric current if you can and check all three pumps at the same time.

Remember - More details = better answers
Also: If you get a response it's polite to respond to it.

### RE: CHW Pump Pressure

(OP)
@BronYrAur
Yes these are in parallel. As per design Total flow required @ common Chiller supply header is 223 l/s. So three pumps in parallel (@ 75 l/s each , all are of same model/capacity)

### RE: CHW Pump Pressure

You may well find that one pump is doing 50 and the other two 85... There are many many threads on this forum about parallel pumping issues and mismatch between supposedly "identical" units.

Lik eI said - post the pump curve if you have it and also try and see how many amps each pump is taking when operating in parallel. It's sometimes easier to measure Amps than fluid flow.

Remember - More details = better answers
Also: If you get a response it's polite to respond to it.

### RE: CHW Pump Pressure

Have you checked the pump impellers for wear or other variances?

### RE: CHW Pump Pressure

(OP)
You are correct Williard.

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

#### Resources

White Paper - Effects of AIA Quick Guide to UL 489 or UL 1077
The function of a circuit breaker is to provide overload (thermal) and short-circuit (magnetic) protection to a circuit and its downstream components. A circuit breaker functions like an airbag in a car, protecting circuit components and people by tripping the circuit to interrupt the current flow if it detects a fault condition in the control system. Download Now
White Paper - Guide to Integrate Large-Format Additive
As with any new technology, getting into large-format 3D printing begins with investigation. The first question may be a simple one: what does “large-format” mean? For 3D printers, “large” is a relative term. Many extrusion-based (FFF) 3D printers are referred to as desktop machines, because they fit on table space. Some of these have very respectable build volumes – but when it comes to “large-format,” the machines will need their own dedicated floor space. Large-format 3D printers have significant build volumes and are most often found in professional settings, like manufacturing facilities and R&D centers. Download Now

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!