×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# NPSH in pipeline boosting pumps2

## NPSH in pipeline boosting pumps

(OP)
How do I calculate the NPSHa in a pipeline boost application (no tanks as suction feed)? Say for instance, that pressure I expect in the suction point is 200 psig...

Thanks

### RE: NPSH in pipeline boosting pumps

The NPSHA is the pressure at the pump suction above the fluid's vapor pressure.

So, take your suction pressure (in psiA) and subtract the vapor pressure of the material (in psiA).  That will give you the pressure (in psi) above the fluid's vapor pressure.

Multiply by 2.31 and divide by the specific gravity just like if you were calculating the head for a pump.  The 'head' will be in feet of fluid and is the NPSHA you have.

If the minimum suction pressure for the pump is less than the 200 psig (assuming this is the normal operating pressure), you should use the minimum suction pressure in the calculation along with the maximum vapor pressure.  In all reality, you'll likely have lots and lots of NPSHA.

### RE: NPSH in pipeline boosting pumps

See the NPSH(A) calculation can be done by the following formula:

in case the storage tank is open to atmosphere:
NPSH(A) = P (atm)+ pressure due to height of liquid in storage tank - vapour pressure of the pumped liquid at working temeperature and pressure-pressure losses in the piping from storage tank to suction nozzle of the pump.

in case the storage tank is  not open to atmosphere:
NPSH(A) = pressure due to height of liquid in storage tank - vapour pressure of the pumped liquid at working temeperature and pressure-pressure losses in the piping from storage tank to suction nozzle of the pump.

take care of the units and maintain a consistency.

p (atm) = atmospheric pressure
pressure due to height of liquid in storage tank = density x acceleration due to gravity x height
vapour pressure can be taken from charts or tables
pressure losses in piping can be calculated using several formulae available in handbooks.

hope this helps.

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

#### Resources

White Paper - Implementing a Multi-Domain System
IoT systems are multi-domain designs that often require AMS, Digital, RF, photonics and MEMS elements within the system. Tanner EDA provides an integrated, top-down design flow for IoT design that supports all these design domains. Learn more about key solutions that the Tanner design flow offers for successful IoT system design and verification. Download Now

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!