Air trapping through suction pipe when switch off the condenser pump. During switch off all water reurened to the cooling tower, Cannot be possible to change the piping configuration. Thinking an idea by fitting NRV closed to cooling tower outlet pipe to hold the water in suction pipe during the off period. Pipe size 16 inch. Any other suitable ideas…find the approximated sketch
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Since the later 1980s, manufacturing companies have seen over 3 percent in labor output year on year, with most of this productivty enhancement occuring because of the optimization of repetitive tasks. Download Now