A Contractor was to splice two 1000 Amp busways together. The busways are about 100 feet apart. He used conduit but put each phases conductors in a separate conduit. I'm aware of the NEC Handbook that says it's essential to run A-B-C-N in each conduit, but it doesn't really state it like this in the actual NEC. Is there a big problem here?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Improving the battery life of our devices remains one of the tech industryâ€™s biggest challenges, and the most inefficient draw on power comes from the display, more specifically, the backlight that illuminates most displays. Download Now