×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# Pumps in parallel vs series - Flow vs head3

## Pumps in parallel vs series - Flow vs head

(OP)

However, for parallel case, not sure what I'm missing but find it not so intuitive to visualise why heads are not added. How the energy is dissipated in this case, by overheating the pumps?

There could be two cases in parallel case,
I. Both pumps are identical
II. One pump is bigger (higher head and flow capacity)

### RE: Pumps in parallel vs series - Flow vs head

Head is added in both cases. In the diagrams, you need to follow the system curve from points 1 to 3.

I used to count sand. Now I don't count at all.

### RE: Pumps in parallel vs series - Flow vs head

In the case of parallel pumps, the point in the piping where the separate flows combine must be an equal pressure condition in the system, therefore equal head seen by the pumps.

Ted

### RE: Pumps in parallel vs series - Flow vs head

In the parallel case, there are two options, as you stated, that the pumps may or may not be the same head. So, the total flow is added from two pumps based on the discharge pressure of each pump. If both pumps with the same head, the total flow is theoretically equal to two pumps flow. The reality is that the discrete pressure may be increased a little to accommodate the increased pressure drop because of the higher flow.

### RE: Pumps in parallel vs series - Flow vs head

An easy way for non process engineers to visualise this is to equate pump head with electrical voltage across the terminals on a battery, while flow is equivalent to current.

### RE: Pumps in parallel vs series - Flow vs head

Parallel pumps must be similar in size and duty. Otherwise they will fight each other.

### RE: Pumps in parallel vs series - Flow vs head

3
A common misconception when looking at parallel centrifugal pumps is that the pumps pump a fixed volume, e.g. say you had two "750GPM @ 150 ft hd" pumps, connecting them in parallel WON'T give you 1500 GPM @ 150 ft because the resistance to flow in the pipe increases.

If the pumps are identical then they might do, say, 1200 GPM @ 165ft, 600 GPM each. Hence they will use LESS power than if they were operating individually. So there is no "energy being dissipated", because it is not being used in the first place. However there will be an energy increase in frictional losses because you're flowing more fluid faster through the same size pipe. It all depends on the intersection with the system curve. If you added in my example a third 750 GPM pump, total flow might only go up by 200 GPM due to the system curve, hence <500 GPM each.

In general you tend to see series pumping when there is either a high static head or pressure to overcome and one pump can't supply that head or when the head requires changes but the flow doesn't.

Parallel pumps work well when the system curve is quite flat or where the static head portion is quite high compared to the frictional losses.

Remember - More details = better answers
Also: If you get a response it's polite to respond to it.

### RE: Pumps in parallel vs series - Flow vs head

Draw a parallel pump curve using actual or proposed single pump curves. Calculate the actual or design system curve and plot it on the parallel pump curve. If pumps are not the same design you can't draw a parallel curve which tells you don't operate them at the same time. Some pump selections for parallel pumping results in one pump delivering 85 to 90 percent of design flow with one pump running. Depends on pump selection and how close actual operating conditions match design.

### RE: Pumps in parallel vs series - Flow vs head

wayne3298 said, "Draw a parallel pump curve using actual or proposed single pump curves. Calculate the actual or design system curve and plot it on the parallel pump curve. If pumps are not the same design you can't draw a parallel curve which tells you don't operate them at the same time"

I don't know what you meant by this, can you clarify?

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

#### Resources

White Paper - PLM and ERP: Their Respective Roles in Modern Manufacturing
Leading manufacturers are aligning their people, processes, and tools from initial product ideation through to field service. They do so by providing access to product and enterprise data in the context of each personâ€™s domain expertise. However, it can be complicated and costly to unite engineering with the factory and supply chain. Download Now
White Paper - Medical Device Design Control
Medical device product development is a highly integrated and regulated process. Implementation of a requirements tracking solution requires attention to a variety of nuanced topics. When presented with the task of tracking the many concept relationships in a project of this type, the initial software solution of choice tends to be a two-dimensional text systems. Download Now

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!