Gentlemen, can a ground fault on the primary side of a delta/delta main transformer (1MVA, 13200/380) be seen/detected on the secondary side of the transformer? I say, NO.
We would like to avoid MV rated PTs to detect a utility ground fault. No high side Wye-G PTs are installed.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.