I have a situation where I need to move the motor termination box to the top of the motor, because of clearance issues. The motors are 480V, 200HP, TEFC. I contacted a motor shop and they can make a duct from the side of the motor to the top of the motor where I can re-attach the motor termination box. My question is the motor termination box considered pat of the electrical motor? I am wondering if I will run into a UL issue by doing this?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Manufacturers are at a critical juncture. Either they evolve their product processes or get disrupted by new competitors who have been built from the ground up to develop complex systems and products defined by software. Download Now
Savvy engineers have eagerly anticipated the impact of virtual reality (VR) on robot programming technology, as it can dramatically increase productivity by empowering engineers to do their jobs safer and more efficiently. Download Now