Our contractor installed a multiconductor cable in a tray. I was told per NEC, we have to increase size of existing bare tray grounding cable because it's smaller than our newly installed cable equipment ground. Is that correct? Each cable in this tray has its own equipment ground.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.