As per NFPA, the total inside and outside hose allowance for extra hazard group is 500 gpm. My understanding is this allowance is only for the inside and outside hoses which excludes any fire hydrant allowance (class-1 standpipe). For fire hydrants, we need to add additional allowance of 500gpm.
I would like to know the above considerations are in compliance with NFPA standards.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Improving the battery life of our devices remains one of the tech industryâ€™s biggest challenges, and the most inefficient draw on power comes from the display, more specifically, the backlight that illuminates most displays. Download Now