×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Log In

Come Join Us!

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
To Your Posts
• Keyword Search
• One-Click Access To Your
Favorite Forums
• Automated Signatures
On Your Posts
• Best Of All, It's Free!
• Students Click Here

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

Students Click Here

Louvre sizing

 Forum Search FAQs Links MVPs

Louvre sizing

(OP)
As per ASHRAE Fundamentals 2009 Chapter 21 Table 8, the design "face" velocities for determining the louvre size is 2m/s for Intake and 2.5m/s for exhaust. Can anyone clarify how to use these velocity values in sizing the louvres?

For example, if 5000 CMH (1.39 m3/s) of air has to be exhausted out, which one of the following is correct by considering, 2.5 m/s as the face velocity?

1) Face area of the louvre with 50% free area is 1.39/2.5 = 0.556 m2 (which means, free area of the louvre is 0.258 m2 and the velocity of exhaust air in this free area is 2.5 * 2 = 5 m/s)

OR

2) Face area of the lourve with 50% free area is 1.39/(2.5*50%/100%) = 1.112 m2 (which means, free area of the louvre is 0.556 m2 and the velocity of exhaust air in the free area is 2.5 m/s.

So, the ASHRAE guideline velocity is the face area velocity or free area velocity?

Thanks in advance.

RE: Louvre sizing

face velocity is useless, each louver has different % of free area.
Take manufacturer data that shows pressuredrop and rain entrance (for intake louver). you don't want to have rain and snow be drawn in.

ASHRAE books have a lot of good stuff, but also a lot of outdated garbage. they go by the least cheapest manufacturer so no one is offended.

RE: Louvre sizing

there is no such thing as "face area velocity". air flows through effective area, that is why it's called effective area.

Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Reply To This Thread

Posting in the Eng-Tips forums is a member-only feature.

Click Here to join Eng-Tips and talk with other members!

Close Box

Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!

Already a member? Close this window and log in.