×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# refrigerant weight

## refrigerant weight

(OP)
Hi there

hope everybody is fine.

Please, I'd need an hint as follows.

is there a literature reference or formula in order to calculate thew weight of refrigerant contained in a condenser and an evaporator ?

Ex:
In a condenser with condensing temperature of 122F, with R410A, how much is the weight of refrigerant ?

it can't be the volume for specific weight, since I have a phase change.

Please, can anybody help me ?

thanks !

### RE: refrigerant weight

(OP)
Hi !
I am afraid that I'd need more help.
My point is: I know a mass flow, but I don't know the mass or the volume that has been inputted.
Would you be so kind and make me an example of calculation ?

Thanks !

### RE: refrigerant weight

The mass flow past any point in the (recirculating) system will be identical.

The volume flow at any point is simply the mass flow times the specific volume.

Specific volume is available from tables except for saturated mixture states (eg condenser and evaporator) where quality is unknown but could be inferred as linear between 0 and 1 whit distance travelled along the heat exchange path. The section of the HX where mixed phase exists can be approximated since T will be constant throughout that section.

je suis charlie

### RE: refrigerant weight

(OP)
Many thanks
@ gruntguru
I have a massflow (mass/unit of time).

1) It is not clear to me how to pass from mass flow to mass.
2) shall I then make an integration along the condenser length on quality ?
3) how shall I consider the calculation for refrigerants with glide ?

Many question, but thanks to your help things are getting step by step more clear !!

### RE: refrigerant weight

To estimate total mass you can probably ignore sections containing vapor. Calculate the total volume of sections containing liquid and divide by the specific volume of the refrigerant.

je suis charlie

### RE: refrigerant weight

Gruntguru has the approach but I'll go a little further to his approach. Shut down the refrigeration system for a period of time so that the system is under constant pressure and temperature, the ladder of which may be a little difficult depending where the equipment is located. Knowing the type of refrigerant, you can approximate the specific volume from chart or graph and then calculate the mass.

### RE: refrigerant weight

The equipment manufacturer would have the data on the required refrigerant charge for the system. Clarify from them how much correction to add for longer refrigerant pipe runs than their normal allowance.

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!