×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

continuous recirculation loop

continuous recirculation loop

(OP)
I have a trouble, we have to design a continuous recirculation loop with a water storage tank and a pump with a bladder type tank. The discharge pressure should be 40 - 60 psi (requirements of equipment connected to the line), and the pressure at the return line must be near 22 psi (requirements of equipment). But the losses in the system are 32 psi. The question is if I could set a relief valve at the last point of the return line, which open at 22 psi.  Could it work right?

RE: continuous recirculation loop

sargon:

A reliev valve is a connection to atmosphere with is an out for your system which would mean its not a closed loop anymore.  What is the system used for and are there any demands on the system that will use flow?  The use of the bladder tank will mean that pressures will keep stable around your set point so the demands will be critical to meeting your suction pressure requirement.

BobPE

RE: continuous recirculation loop

Sargon!

You can do it with specifying your back pressure (what ever it is) on the relief valve when you order it. There are Back Pressure Control Valves already available. Try one.

Regards,

Repetition is the foundation of technology

RE: continuous recirculation loop

Not sure what the problem is:  If you provide a pump (or pump and throttle valve) that produces 54 psig, you'll have enough pressure at your first use point, and with a drop of 32 psi you will have enough at your last use point = 22 psig. (?)     If however, the flow in the system will vary due to different demands then the 32 psi will vary.  To keep the presure to the last piece of equipment relatively constant at 22, you would install a  pressure regulator in the branch from the loop to that equip. set at 22 psig.  (a relief valve is not appropriate)   In that case the pump can be set to discharge as high as the 60 psig

Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Resources

eBook - Functional Prototyping Using Metal 3D Printing
Functional prototypes are a key step in product development â€“ they give engineers a chance to test new ideas and designs while also revealing how the product will stand up to real-world use. And when it comes to functional prototypes, 3D printing is rewriting the rules of whatâ€™s possible. Download Now

Close Box

Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!