The issue is regarding the orientation of the intermediate cross ties within a boundary element. Per ACI 188.8.131.52, the crossties shall be alternated end for end for proper confinement (see section 184.108.40.206c for required transverse reinforcement in a boundary element). This week we found out that the cross ties were installed incorrectly for approximately 8 boundary elements; where, the 90 degree hooks were not alternated within the shear wall boundary elements. We have been looking for a solution to provide confinement that satisfies ACI 220.127.116.11; this has included, FRP wrap/anchors (FYFE, BASF), reinforced concrete jacket, but each solution has not been successful. Has anyone ever run into a situation where this has occurred? Is there anyway to justify/provide confinement after a wall has been cast. I appreciate your feedback.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Improving the battery life of our devices remains one of the tech industryâ€™s biggest challenges, and the most inefficient draw on power comes from the display, more specifically, the backlight that illuminates most displays. Download Now