I'm a trouble man for a utility company. We have a 14.4 phase to ground 26 phase to phase line. The problem is a 277/480 bank. Under normal source conditions there is no problem. When we switch the line out to another substation our phase to ground voltage is good but the phase to phase goes haywire. 515 480 444. ?? It's a bank of 3 250 kva transformers on a rack. The further I get from the station the worse the voltage gets. I have a 3 phase pad mount another mile down the road and the voltage is even worse. I know there's at least 3000 Kvar of capacitance on the distribution circuit. The customers equipment trips off line immediately when we switch to the other substation. There alarm is an current imbalance of 30% or greater for 1 second. Any help would greatly be appreciated. Thanx
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
3D scanning is revolutionizing how engineers digitize parts. Not long ago, if you had a physical object and wanted to create a 3D model of it, you had one option: bust out the calipers, measure every nook and cranny, and create the model yourself. Download Now
Material selection can be a guessing game, but it doesn’t have to be. If you’re an engineer looking to quantitatively analyze a material to determine if its properties fit your application, then you’ll need to be ready with a wide range of facts. Download Now
Teach pendants are a critical part of the factory environment as they act as the human/machine interface for industrial robots. But since teach pendants are handheld, they are under a greater risk of damage due to falls. Download Now
Product development in most companies requires a sequential iterative process to come up with the right product. It can be time-consuming and time is a resource that is in the shortest supply. Download Now