×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# HV Motors - Heating and Cooling Time Constants

## HV Motors - Heating and Cooling Time Constants

(OP)
Can some one suggest where to get typical heating and cooling time constant information for large HV motors, say, 1000kW. The motors are old and manufacturer's data sheets are not available.

### RE: HV Motors - Heating and Cooling Time Constants

My plant has many large motors which are continuously monitored for winding temperature and bearing temperature.

I'll assume you are talking about winding temperature.

Two examples in the horsepower range you mention:
1 - 800hp 120rrpm vertical air-cooled motor.
Motor is initially steady state at 119F (space heaters keep it above ambient). Ambient temperature is initally 81F
12:06am motor started -  T=119F
12:11 - T=152F
12:16 - T=167
12:21 - T=177
12:26 - T=185
12:31 - T=190
12:36 - T=196
12:41 = T=201
12:46 - T=205

Getting tired of 5 minutes readings. Here are some wider spaced readings:
1:06AM - T=216
1:21 - T=220
2:06 - T=226
3:00 - T=229
4:00 = T=229F
Final ambient temperature is 82F (relatively constant).

At the moment I don't have the energy to figure out the time constant. You are welcome to if you'd like.

### RE: HV Motors - Heating and Cooling Time Constants

(OP)
Electripete,

Thanks for the info. The Heating Time Constant comes to 15minutes (hope I am right).

Could you please pass the info for calculating the Cooling Time Constant for the motor.

Thanks once again,

### RE: HV Motors - Heating and Cooling Time Constants

Suggestion: The manufacturer recommends a number of starts/stops per specified time period. These are linked to cooling/heating time constants.

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!