I know that code clearance for a transformer and panel is 3'I believe, don't have NEC with me. But the question is people at our shop want to move the painters stuff into an area were there is a transformer and two panel box's 120 and 480, the area is open and by the maint dept. My question is how far according to codes do the paint cabinets and the bench were the painter will be using thinners and such have to be from the electrical items i have stated.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
When it comes to using an FDM 3D printer effectively and efficiently, choosing the right material at the right time is essential. This 3D Printing Materials Guide will help give you and your team a basic understanding of some FDM 3D printing polymers and composites, their strengths and weaknesses, and when to use them. Download Now
Simcenter STAR-CCM+ makes simulation accessible to process engineers with limited simulation experience but strong process knowledge. This flood of knowledge and skills will make the industry more cost efficient, less polluting and ultimately more innovative. Download Now
The need to reduce exploration and development costs has never been more important to the future of the oil and gas industry. In this special report we present how engineers and scientists from leading oil and gas companies are deploying Siemensâ€™ simulation software in the design and operation of a range of oil and gas products and systems. Download Now