I know that code clearance for a transformer and panel is 3'I believe, don't have NEC with me. But the question is people at our shop want to move the painters stuff into an area were there is a transformer and two panel box's 120 and 480, the area is open and by the maint dept. My question is how far according to codes do the paint cabinets and the bench were the painter will be using thinners and such have to be from the electrical items i have stated.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
This ebook covers basic tips for creating and managing workflows, security best practices and protection of intellectual property, Cloud vs. on-premise software solutions, CAD file management, compliance, and more. Chapter 2 covers cybersecurity and answers the question: How do you secure your files and documents? Download Now