what is reason for minimum conductor size that can be run in parallel (other than economic and labour intensity). I am working to marine/offshore rules that state minimum c.s.a that it is permitted to start running conductors in parallel is >10mm.sq.
someone asked me if they could run 2 x 1mm.sq cables instead of 1 x 1.5mm.sq.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
This ebook covers tips for creating and managing workflows, security best practices and protection of intellectual property, Cloud vs. on-premise software solutions, CAD file management, compliance, and more. Download Now
A/E firms have a great opportunity to lead the world into the future, but the industryâ€™s greatest assetâ€”real-time dataâ€”is sitting wasted in clunky, archaic ERP platforms. Learn how real-time, fully interactive dashboards in a modern ERP allow you to unlock data that will shape the future of the world. Download Now