×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# determining pressure drop across valve

## determining pressure drop across valve

(OP)
i need to determine the max volume (capacity) of nat gas across a couple of valves.  this seemed simple enough, get the valve constant from mfg and plug into eqn:
Cv = (Q/1360) * [(2*G*T)/(deltaP*(P1-P2))]^0.5

i contacted one mfg and got their valve constant, but the other mfg (Grove) told me there was no constant for their valve!  just use equivalent length of pipe for that diameter pipe.

that "other" valve is a Grove B5 12" ball valve.  any idea on best way to calculate maximum flow (or pressure drop) across this valve?

my understanding is to assume a max pressure drop of 50% of inlet pressure and then use that to determine flow across valve.  does this seem reasonable? or does anyone have other ideas or corrections?

thanks,
kahlil

### RE: determining pressure drop across valve

Umm, using a dP of 50% of the inlet pressure will give you approximately sonic flow through the valve and that will be the maximum flow.  I'm not sure what you are trying to do with this number though.  The maximum dP is more likely going to be set by the piping system the valve is installed in.

For the 12" ball valve, using your approach, the flow would be huge.  The L/D for a ball valve (which is what the manufacturer is suggesting) is about 3 * turbulent friction factor for an full port ball valve.  The upstream and downstream piping for this case is going to set the flow rate, not just the valve (and the upstream/downstream piping is likely going to have a similar effect on the other valve as well).  The manufacturer should have Cv values for this valve, talk to someone else.  At the very least, they should have flow versus dP data and you can calculate the Cv off that.

### RE: determining pressure drop across valve

If you provide me with the pressure class I can provide you with the Cv.
Jim Dietrich
Dresser Flow Control

### RE: determining pressure drop across valve

(OP)
thanks jim.  valve is 600#.  i estimated flow to be 20,350,735  scfh.

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!