We were tasked to design a new pump station that will discharge into an existing (common) 4” forcemain that runs past the new PS site. I have checked the existing pump station upstream and with our new station running it appears that the existing pump station will be locked out. We’re not a big fan of common forcemains so our solution is to modify the existing FM to dump into our new receiving manhole. We'll then connect a new FM from our new station to the existing FM. We'll then size the new pump station to pump the existing pumps design discharge + 1.8 x calculated new sewer inflow. In addition we’ll look at 2.5 x new area inflow with no additional flow from the existing pump station. I would be interested to hear others opinions/remarks.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Improving the battery life of our devices remains one of the tech industryâ€™s biggest challenges, and the most inefficient draw on power comes from the display, more specifically, the backlight that illuminates most displays. Download Now