What is the pressure drop calculation method for an exhaust ductwork system where multiple exhaust fans discharge into a common header, and the combined E/A duct run out the building? Can you assume the friction is the same as a single fan system? Also, how do you size the fan with the back pressure from the other fans?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.