×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# affinity laws, axial fan

## affinity laws, axial fan

(OP)
Dear all,
Hope somebody can help me to clairfy this topic.
I have measured the air flow, rpm and absorbed power of a three phase axial fan at two different fan speed – delta and star connection.
I will call 1 and 2 this two conditions..
What puzzles me is, if I consider affinity laws
- equation (air flow 1/air flow 2) = (n1/n2) is respected. The two ratios are practically identical.
- equation (absorbed power 1/ absorbed power 2) =  (n1/n2)^3 is not respected. (the power is the total absorbed power)
There is a large difference between the two ratios.

Please, is there something I am missing or is it due to a wrong measurement ?
Many thanks

### RE: affinity laws, axial fan

So, you are changing the voltage, which changes the slip, which slightly changes the speed, and without changing the system, you are observing changes in flow rate and input electric power, correct?

Some things to consider:

1 - The pump/fan laws DON'T tell us what happens to the operating point with change in sped. They tell us what happens to the pump curve.  To convert that knowledge of change in pump curve to knowledge of change in operating point, we would need to know sometihng about the SYSTEM characteristic curves (the operating point is the intersection).  As it turns out, ONLY if the system characteristic curve obeys DP~flow^2 do these relations apply directly to the operating point.
2 - affinity laws apply to incompressible fluid.  For a fan, they are pretty close if the dp is far less than the absolute pressure (so that pressure and density don't change by a large factor). They are not good if the dp is a sizeable fraction of the absolute pressure, such that density is not even close to constant.
3 - affinity laws apply to bhp, but you are measuring input power I think.  If there is significant change in efficiency then you have an error.

=====================================
(2B)+(2B)'  ?

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!