×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# Sizing Open Vents

## Sizing Open Vents

(OP)
How do you go about calculating the maximum air flow through an open vent on a storage tank assuming it is a swan neck breather (so 2 elbows and 200mm of pipe) when the tank is discharging and filling?

I have heard that you should carry out a pressure loss calculation but I do not know where to start.

For arguments sake how would I find what size swan neck breather to install on a tank venting at 200m3/hr?

Thanks

### RE: Sizing Open Vents

For petroleum storage, API-2000 requires that conventional vents be flow-tested.

The ASHRAE handbooks have some duct-flow and fitting-loss information that can be applied otherwise.

### RE: Sizing Open Vents

The calculation is really trial & error.
The first step is to determine the tank's pressure and vacuum rating.
Second step is to assume a pipe diameter.
As an example, if the pressure rating is 10" h20 and assume 2" pipe.
The friction loss through the 2" swan neck would need to be less than 10" h20 at 200m3/hr flow.
If the fricion loss is too high, redo the calculation for larger pipe.
Similar logic for the vacuum side.

JStephens is correct -- use a calibtaed device if you need to follow API-2000 standards.
Years ago, Groth used to sell calibrated Swan neck vents
but today I do not know where to purchase similar hardware.
Otherwise Note that OSHA requires a 100% safety factor be applied for uncalibrated venting devices.
So the calculation would need to be at 400m3/hr flow to satisfy OSHA.
Additionally, most swan necks I have seen have bug screens which typically reduce the flow area to 2/3 of base pipe area.
I typically add one pipe diameter if a bug screen is used.

Normal filling and pumpout is typically small flows compared to other ways to overpressure a tank.
Consider also nitrogen pad requlator failure.
Consider also the maintenance practice of clearing connecting pipe by air blowing.
A 3/4" air hose 10-ft long with wide open block valve can generate alot of pressure which must be vented.

### RE: Sizing Open Vents

Also consider icing up of the bug screen if you are in a cold climate.  Using 3/4" mesh screen should help this while still excluding birds.

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

#### Resources

Low-Volume Rapid Injection Molding With 3D Printed Molds
Learn methods and guidelines for using stereolithography (SLA) 3D printed molds in the injection molding process to lower costs and lead time. Discover how this hybrid manufacturing process enables on-demand mold fabrication to quickly produce small batches of thermoplastic parts. Download Now
Examine how the principles of DfAM upend many of the long-standing rules around manufacturability - allowing engineers and designers to place a partâ€™s function at the center of their design considerations. Download Now
Taking Control of Engineering Documents
This ebook covers tips for creating and managing workflows, security best practices and protection of intellectual property, Cloud vs. on-premise software solutions, CAD file management, compliance, and more. Download Now

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!