Does a flexible cable carrying 30 VDC (Discrete Signal) Fall under NEC 400.8 or NEC 725? Is NEC 400.8 written for temporary and extension cords that carry 120 VAC and above? Is NEC 725 for power limited cables. I mounted a flexible cables to the wall. The cables are discrete 30 VDC that monitor limits switches. I was told that this is a code violation. Did I break code?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.