×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# short circuit torque

## short circuit torque

(OP)
I have a asyncronous generator 500 kw and 500 rpm speed, and i´´m designing a fly wheel for it, and the short circuit torque given by the manufacturer is 96 KNm, and i think that maybe is too much... how could i know if this is true..or no so true.... does somebody could help me.... I´´m not very confortable with this questions.... thanks.

### RE: short circuit torque

You need to use the value given by the manufacturer, unless you have a lot of liability insurance.

You might ask them to verify, but in the end, you must use their value.

### RE: short circuit torque

(OP)
but in your opinions, what do you think? is too much?? and why it could be a high value..?
what are the elements that make it to be high? reactance?
thanks

### RE: short circuit torque

I agree with dpc you have to follow the Manufacturer indications.
For a very rough appreciation let's take as follows:
Prime motor [DG or wind or else] rated torque as Generator rated torque: Trated= 60*1000/2/PI()*P/rpm=9549.3 Nm.
For a similar induction motor the inertia moment will be J= 60 Kg.m^2.Let's say the prime motor has the same inertia moment.
Let's suppose, up to generator breaker will trip time=0.07 sec and within this time the generator will positively stop.
The possible torque on the Generator shaft will be Te=(Jgen+Jmot)dw/dt+Trated
dw=(2*pi*rpm/60-0)= 52.36 rot/sec
Te=2*60*52.36/.07+9549.3=102000 Nm=102 kNm.

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!