Metalic pipe wall thickness is determined by the "Code of Record" used for the design. This is frequently determined by the local laws and statutes.
For systems over 15 psig that are not specifically designated as plumbing, fuel gas, drainage or fire protection, ASME B31.1 Piping Code typically is invoked by local laws and statutes. B31.1 provides formulae and rules for determining "minimum wall" thickness for a particular pipe diameter, material and design temperature. (Section 104.1)
A corrosion allowance, typically 1/16 inch, must be determined by the piping system designer and included in the calculation. If the pipe is to be threaded, an allowance must also be made for this.
The minimum wall thickness is compared against standard schedule piping and one "piping schedule" (wall thickness)is selected for the entire system.
Flanges and valves of compatable materials are selected based on temperature-pressure tables. (see ANSI B16.5 and B16.34)
Learn methods and guidelines for using stereolithography (SLA) 3D printed molds in the injection molding process to lower costs and lead time. Discover how this hybrid manufacturing process enables on-demand mold fabrication to quickly produce small batches of thermoplastic parts. Download Now
Examine how the principles of DfAM upend many of the long-standing rules around manufacturability - allowing engineers and designers to place a partâ€™s function at the center of their design considerations. Download Now
Metal 3D printing has rapidly emerged as a key technology in modern design and manufacturing, so itâ€™s critical educational institutions include it in their curricula to avoid leaving students at a disadvantage as they enter the workforce. Download Now
This ebook covers tips for creating and managing workflows, security best practices and protection of intellectual property, Cloud vs. on-premise software solutions, CAD file management, compliance, and more. Download Now