where V is velocity in fpm W is massflow in lbs/hr sp. vol is the specific volume of the steam ID is the internal diameter of the pipe
Crane also give a couple of nomographs that allow the novice to "graph his way" to a solution. (I have always hated nomographs.... They are an instrument of the devil)
What size pipe do I need for 20,000 lbs/hr of 100 psig saturated steam ?
Using a sp. vol of 3.875 and trying various pipe sizes we find out that a 6 inch, sch 40 pipe (ID=6.065) gives us a velocity of aprox 6457 fpm and is the appropriate size for this service.
(It should be also pointed out, that selected steam piping systems may require sizing by another criteria. The systems that typically requires a close evaluation are the "Main Steam" and "Hot Reheat Steam" to and from steam turbines.)
(These systems typically transport superheated steam and are sized based on the economic value of the pressure drop. Other criteria imposed on the design of the system is 2-5% maximum pressure drop between the boier steam drum and the turbine inlet valve.)
The superb Crane manual can be purchased for about $US30 bucks.... Any engineering book in a twenty sixth printing is wise investment
This ebook covers tips for creating and managing workflows, security best practices and protection of intellectual property, Cloud vs. on-premise software solutions, CAD file management, compliance, and more. Download Now
A/E firms have a great opportunity to lead the world into the future, but the industryâ€™s greatest assetâ€”real-time dataâ€”is sitting wasted in clunky, archaic ERP platforms. Learn how real-time, fully interactive dashboards in a modern ERP allow you to unlock data that will shape the future of the world. Download Now