×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# HVAC/R engineering FAQ

## Sizing Compression Tanks

 How do I correctly size a compression tank? by Yorkman faq403-1256 Posted: 2 Aug 06 (Edited 25 Aug 06) The sizing of compression tanks for closed loop hydronic systems can be calculated by using one of these two formulas.The high and low pressures are going to be determined by two factors. The pressures at the tank connection are selected as follows;    The low pressure at the tank connection, is selected to hold a positive pressure at the highest point in the system usually about 10 psig, when the system is cold(ie;50°F)in the case of a heating system.    The high pressure is usually set by the maximum pressure allowable at the safety relief valve(s) without opening them, at operating temerature.  In the case of a chilled water system the reverse will be used. The high pressure will be when the system is off(ie;90°F), and the low pressure will be when the system is at operating temperature.     The formula used will depend on the type of tank you are selecting.  For a closed tank with an air/water interface use;Vt=Vs{[(v2/v1)-1]-3σΔt}÷[(Pa/P1)-(Pa/P2)]For a diaphram tank use;Vt=Vs{[(v2/v1)-1]-3σΔt}÷[1-(P1/P2)]Where;Vt=volume of tank,gal.Vs=volume of water in system,gal.Δt=(t2- t1),°Ft1=lower temperature°Ft2=higher temperature°FPa=atmospheric pressure psiaP1=pressure at lower temperature, psia P2=pressure at higher temperature, psiav1=specific volume of water at lower  temperature ft3/lb    v2=specific volume of water at higher  temperature ft3/lbσ=linear coefficent of thermal expansion,in/in*  °F=6.5 x 10-6in/in*°F Copper=9.5 x 10-6in/in*°F SteelThese are the methods used in the ASHRAE Systems Handbook Back to HVAC/R engineering FAQ Index Back to HVAC/R engineering Forum

#### Resources

Low-Volume Rapid Injection Molding With 3D Printed Molds
Learn methods and guidelines for using stereolithography (SLA) 3D printed molds in the injection molding process to lower costs and lead time. Discover how this hybrid manufacturing process enables on-demand mold fabrication to quickly produce small batches of thermoplastic parts. Download Now
Examine how the principles of DfAM upend many of the long-standing rules around manufacturability - allowing engineers and designers to place a partâ€™s function at the center of their design considerations. Download Now
Taking Control of Engineering Documents
This ebook covers tips for creating and managing workflows, security best practices and protection of intellectual property, Cloud vs. on-premise software solutions, CAD file management, compliance, and more. Download Now

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!