Can anyone tell me what NEC code article or IEEE std. spells out the requirements for earth grounding on industrial control panels? We are in the plastics extrusion business and have many machines that operate on 3 phase 480 power. All of out thermoformers, trim presses and pelletizers come from the OEM with the equipment grounding conductors installed and sized according to NEC specs in article 250. However, I seem to be having a problem when it comes to specific requirements regarding the grounded electrode system. The power comes into each machine from overhead busway fed from 3000 amp switchboard. Do I need a ground rod on each of the machine control panels? Inside the panels are relays, contactors, PLC equipment, motion controllers, power supplies, etc... Any guidance is greatly appreciated.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Todayâ€™s product development cycle is fraught with difficulties. Increased demands for complex functionality and reduced product development windows cause engineering teams to borrow practices from the IT industry, swapping outdated serial workflows for a more flexible and collaborative design method known as Agile Product Engineering. Download Now
Version control is neither a new concept or a new software feature. But with the explosion of digital information, thereâ€™s an even greater need for tight control and management of documents and data. Download Now