I have an application where I want to add concrete encased ground rods on the perimeter of my plant to reduce the copmbined ground resistance. The resistivity of the ground mat or grid conductors is high about 500ohm-m. The resistivity of the concrete encased electrodes will be assumed at 20ohm -m. So my ground rods now become 70ohms instead of around 300ohms. My question is : for the combined resistance in which I use to determine the GPR, I need to use a resistivity for the mutual ground resistance between the ground grid and rod bed. Do I use som,ething between 500ohm-m and 20ohm -m ? or is this not possible due to the inherent cabibility of the formula. The total grid area is about 16,000m2. The concrete foundation cannot be used because it is "insulated" by a vinyl linerunder the entire area. This can't be punctured.
Any good advice is welcome, however I am in a bit of a rush!
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
ENGINEERING.com surveyed 364 product development professionals to glean insights into how their teams are performing today, and what technologies are most useful to support their processes. Download Now
3D printing has quickly expanded beyond the realm of prototyping and into the world of end part manufacturing. Desktop 3D printers need not be used for making parts themselves, but as a secondary process for producing tools. Download Now
Creating tooling for injection molding is an expensive and complex proposition. Until recently, the only way to avoid tooling defects causing air traps, voids, shrinkage and the like was to employ a time-consuming and tedious physical prototyping process. Download Now