I looking for a loading guide for distribution transformers. At what point is a transformer overloaded? At nameplate KVA, at 20% over nameplate? How does the seasonal peak factor in? Mfgs tend to recommend not loading beyond the nameplate KVA. What about "degrees C rise"? -- Thanks.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.