I work at a power plant and had two separate occasions where a 3 phase 480VAC 150HP delta connected motor tripped on ground fault (valid). A 3 phase 480VAC 150HP wye connected motor also nuisanced tripped (not valid). Both motors are connected to a ITE/ABB Kline loadcenter with a 13.8KV/480VAC delta/wye neutral grounded 1000KVA transformer. Ground fault protection for both provided by a ITE GR-5 ground fault relay and type GS ground sensor (core balance or "window" type CT). Relay pickup is 50A and time delay is .033 seconds. Would like some suggestions on what is causing the wye connected motor to also trip on ground fault when the delta connected motor has a valid ground fault.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
The automotive parts aftermarket is a 2 trillion-dollar business. Major OEMâ€™s like General Motors are eager to win a substantial portion of that market in one of the most difficult supply chain systems in the world. Download Now
Designers in every industry are being pushed to produce larger and more complex product assembles. Add to that the demands that new software features place on your hardware, and you can be in for some serious performance issues. Download Now