I have always wondered as to why does a circuit breaker in the IEC World have so many short circuit breaking capacities such as Ics(service short circuit breaking capacity), Icu(ultimate short circuit breaking cap), Icw (short circuit breaking capacity). After running an ETAP Programme we reach an initial symmetrical short circuit current (say 40 kA) which in turn determine the short circuit rating of the switchgear for 1sec/3 sec( I..E 40kA for 1 second). Some of the suppliers consider it as the prospective short circuit current and match the Icu rating of the breaker( 40kA) to be used on such a switchgear . Shouldn't they select Icw rating of the breaker to match the switchgear short circuit withstand current for 1 sec. Your suggestions will be of great help.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
The automotive parts aftermarket is a 2 trillion-dollar business. Major OEMâ€™s like General Motors are eager to win a substantial portion of that market in one of the most difficult supply chain systems in the world. Download Now
Designers in every industry are being pushed to produce larger and more complex product assembles. Add to that the demands that new software features place on your hardware, and you can be in for some serious performance issues. Download Now