IEE Wiring Regulations * para 537-15 requires an isolating switch to be in a readily accessible position. Does this imply that the cord should be close to the bathroom door or would it be acceptable to locate it close to the wall opposite the door (for practical reasons)?
*Having been retired for a long time I only have 16th Edn for reference!
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Managing reverse logistics and depot repair, or all operations related to the reuse of products and materials, is a growing challenge for B2C and B2B manufacturers, retailers and service organizations. Download Now