We have a single phase exhaust fans (less than 0.75kW) in an Industrial application, I know that disconnect switch should be of 115% of FLC. In Industrial applications for these small exhaust fans, does general snap switches can be considered as disconnect switches or a standard disconnect switch 30A, 240V to be selected? Should the disconnect switch be of 2 pole or 3 pole?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
PCB design is a purposeful process. In essence, every PCB design is a complex puzzle that requires a designer to incorporate critical components and tight schematics into a piece of technology that is governed by rules, constraints and industry standards. Download Now