I'm calculating C Factor of existing pipe in an operating water distribution system. I'm trying account my K losses, (fittings, other factors). I have an 8" inch Ductile Iron pipe and have about 17-1"inch corps tapped into the main throughout. The threads on these corps protrude in the DI pipe approximately an inch to 1/2 inch. How would one account for the resistance coefficient (K) for the 1-inch corp taps in my 8"DI pipe? If the inside liner looks like porcupine from the tapped service line connections this could be throwing my data off?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
PCB design is a purposeful process. In essence, every PCB design is a complex puzzle that requires a designer to incorporate critical components and tight schematics into a piece of technology that is governed by rules, constraints and industry standards. Download Now