Is a soft start considered power conversion equipment by the NEC? I am referring to NEC2011 430.122(B). This section talks about bypass devices. I think the answer is no but would like confirmation. The section says conductors feeding these devices with a bypass needs to be sized on 125% of the input to the conversion equipment or 125% of the motor FLC. This is not a big deal one way or the other for my application but would like to know for future. Thanks!
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.