I have a situation where I need to move the motor termination box to the top of the motor, because of clearance issues. The motors are 480V, 200HP, TEFC. I contacted a motor shop and they can make a duct from the side of the motor to the top of the motor where I can re-attach the motor termination box. My question is the motor termination box considered pat of the electrical motor? I am wondering if I will run into a UL issue by doing this?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Managing reverse logistics and depot repair, or all operations related to the reuse of products and materials, is a growing challenge for B2C and B2B manufacturers, retailers and service organizations. Download Now