There is a discussion with a guy that says his air conditioner fan motor over heated and died because the manufacturer used a 7.5uF instead of the 5uF as stated on the motor. This motor has a run and a start capacitor. I think the cap just opened up or the bearings started to freeze. A friend lets me scavenge old HVAC units for parts and I've seen higher value caps on motors before. Someone told him that the cap has to be within 10% or the motor greatly overheats. I've always thought a little higher was better than being under. Certainly that much higher wouldn't damage the motor. The manufacturer must do it for some reason. Just curious.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Since the later 1980s, manufacturing companies have seen over 3 percent in labor output year on year, with most of this productivty enhancement occuring because of the optimization of repetitive tasks. Download Now