What the factors consider when sizing control valve for oil and water separator outlet , as an example in my process plant , separator oil outlet is 10 inch and installed control valve is 6 inch while the water outlet 8 inch and installed control valve is 6 inch . is the above related to upstream & downstream pressure and flow rate only or there is another fatores? what is the bad effect rather than economic if i want to increase the control valve sizing to decrease pressure losses . another example there is a 4 inch control valve on 12 " discharge of transfer pump which lead huge pressure losses at this control valve so what about if i replace this valve by 8 inch or 10 inch valve
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Since the later 1980s, manufacturing companies have seen over 3 percent in labor output year on year, with most of this productivty enhancement occuring because of the optimization of repetitive tasks. Download Now